|No. 1512||Re: CSE-H55N2 Client - server configuration BACnet MS/TP||2017-08-31|
Thank you for using our products.
In order to find out the reason, we would like to ask some additional information.
1. Could you please describe more detail about your network topology (for example, PC <-> internet <-> CSE-H55N2 <-> BACnet MS/TP device ....)?
2. Could you please tell us how you detect that connection is lost ?
3. Could you please send us the configuration files of both CSE-H55N2 device (on ezManager software, go to "Advanced Menu" -> Export Variables -> save file and send us)
> Ferry wrote:
> On a site i have 1 BACnet MS/TP device, running over a server-client configuration with 2 CSE-H55N2's.
> ~ 4-6 times a day the conection between the two devices get lost.
> On the same plant i have the same configuration with MODbus RTU, works fine.
> The only different is the protocol and the baudrate.
> Modbus is running on 9600 with parity even, Bacnet is running on 19K2 without parity.
> Do i need to do a special setting in the H55N2's?