|No. 1863||Re: Verify Data Rx / Tx||2022-05-03|
Thank you for using our product.
Regarding your question, ezManager has a program called Simple Test Program. This program was designed for users to make a quick test of Serial to Ethernet converter. However, you can use this to send/receive the data on RS-232, Ethernet, or both.
In this case, to monitor RS-232 data, you need to connect CSE-H25 to your PC
via a RS-232-to-USB cable. You can refer to page 32 of the ezManager User Manual for more detail.
As an alternative, you can capture the RS-232 data by using a Telnet program.
The advantages of this way are:
- You do not need to connect the CSE-H25 to your PC via a RS-232 cable.
- CIE-H25 just captures RS-232 data and send it to the Telnet program on PC (via Ethernet port)
For more information, please refer to "6.2 Status Monitoring" (page 38) of CSE-H25 User Manual. Please use "sd" command for data capturing.
> Kevin Roberts wrote:
> I didn't see the info in the FAQ. We have a number of these we use for our Badger Meter gateways. I can connect fine to the CSE-H25, just wondering if there is a way to see that it sending /receiving data on the rs-232 port using ExManaher